DIXEL XR100C PDF
Dixell technology is leading the way in electronic regulation and control in the fields of refrigeration, air conditioning and heating, and retail. Dedication to. Dixell. Installing and Operating Instructions rel /02/ – cod. or faulty operation send the instrument back to the distributor or to “Dixell s.r.l.” (see. Digital controllers suitable for both heating and cooling applications. • Built in RS for connection to Dixell’s monitoring system. • Temperature control can be .
|Published (Last):||14 August 2011|
|PDF File Size:||7.84 Mb|
|ePub File Size:||3.19 Mb|
|Price:||Free* [*Free Regsitration Required]|
Cooling — Differential is above the Set Point Heating — Differential is below the Set Point If a probe fault is detected the display will flash P1 and the controller will automatically cycle the compressor on and off. They can be used to control multiple stages, compressors, condenser fans, heaters or pumps. Generally, these ‘safeguards’ are very inexpensive and may in some situations be looked upon as standard procedure where there is any doubt about the quality of the electrical supply or the effect of associated electrical equipment.
Dixell parametric controllers, fan speed controllers and inverters, compressor controls, EEV drivers, sensors and monitoring systems are trusted around the world.
Click the X to close this notice. Sensor interference and extension of probe cables It is important to avoid running probe cables close to power cables or other electrical equipment and cables that carry or switch heavy loads. The start time for each defrost is stored in non volatile memory, so these will not have been lost.
If there is any risk of water getting behind the front mounting then this must be prevented by the use of a suitable gasket PELE Use the The new value can then be stored either by pressing the SET button or dixe, waiting 15 seconds until the exit time out has expired.
Digital Thermometer XRC V – Thermometer
Defrost time resolution is in 10 minute increments, so doxel Sets the maximum duration time of the defrost Sets the temperature sensed by the evaporator probe, above which the count towards next defrost is suspended as set in parameter IdF Only functions if Smart Defrost is enabled xr100 parameter EdF Sets the evaporator temperature at which the controller will terminate the defrost. Panel mounted controllers have a frontal protection rating of IP Parameter Fnd fan delay now becomes the delay between the start of the 1st and 2nd compressor.
Sets the current day. Most normal supplies are however acceptable but where the supply is also used for large motors, fluorescent lights, etc. Normal display is resumed once the actual xr100cc drops below this point or the time set in this parameter has expired Sets the period of time following the termination of a defrost during which period nothing xr1000c. Sets the number of degrees above or below Set Point 2 at which the load is switched on. Sets the initial temperature alarm delay time on start up so avoiding unnecessary alarms while temperatures stabilize.
Type model name in search bar or visit product detail pages to view corresponding manuals.
Only for XRC with alarm relay: Dixell technology is leading the way in electronic regulation and control in the fields of refrigeration, air conditioning and heating, and retail. Sets the low temperature or pressure alarm level.
This input type must be specified at time of order. When extending probe cables use cable Part No. Tells the controller whether to do an immediate defrost when the power is switched on or to wait for the normal interval time as set in parameter IdF.
Dixell XR100C in USA
The earth connection must be made otherwise the filter will not function.
See page 33 for further details. Sets the display to read out in Celsius or Fahrenheit. This is even more important when extending probe cables. Sets the highest value to which the customer can adjust the Set Point Sets the high temperature or pressure alarm level. Sets the time delay at the end of defrost between an alarm condition being detected and the alarm being signaled.
If this parameter is set to 0. Push SET for 4 secs. H it H 30 mins. Sets the maximum temperature sensed by the evaporator probe above which the controller stops evaporator fans from running Sets the time delay between the end of defrost and the evaporator fans re-starting. Then turn to the parameter list for your particular model, which has all the information you need on the various parameters, their functions and adjustment ranges.
It’s a community-based project which helps to repair anything. This temperature is sensed by the evaporator probe if fitted Sets the interval time between the start of successive defrosts Turns the decimal point on or off.
Use the to alter setting. Setting the ‘smart’ parameter sets the software defaults accordingly.